ZMS Cable世界杯预选赛赛程表 comany mainly provides complete supply services for distributors and suppliers all over the world. Consulting services, purchasing services, transportation services, after-sales services included.
Commonly used laying methods for low-voltage cable lines are: 1 direct buried; 2 laid in cable trench; 3 laid along wall; 4 laid in cable tunnel. The type of low-voltage power cable is mainly selected according to the environmental conditions used and the way it is laid.
BS 7835 (LSZH Version)
世界杯预选赛赛程表Conductor: Plain annealed copper or aluminium complying with IEC 60228/BS 6360. Copper
世界杯预选赛赛程表conductors shall be stranded and aluminium conductors shall be either solid or
世界杯预选赛赛程表Conductor Screen: Extruded layer of semi-conducting cross-linkable compound is applied
世界杯预选赛赛程表over the conductor and shall cover the surface completely. The minimum thickness is 0.3mm
世界杯预选赛赛程表and the maximum resistivity shall not exceed 500 Ohm-m at 90°C.
世界杯预选赛赛程表Insulation: Insulation is of cross-linked polyethylene compound XLPE (GP8) conforming to
世界杯预选赛赛程表BS 7655-1.3 or EPR (GP7), conforming to BS 7655-1.2.
|Nom. Cross Section Area||Insulation Thickness at Nom. Voltage|
|70 – 185||8.0|
Insulaton Screen: Extruded layer of semi-conducting cross-linkable compound is applied
世界杯预选赛赛程表over the insulation. The extruded semi-conducting layer shall consist of bonded or cold
strippable semi-conducting compound capable of removal for jointing or terminating. As an
世界杯预选赛赛程表option, a semi-conducting tape may be applied over the extruded semi-conducting layer as a
世界杯预选赛赛程表bedding for the metallic layer. The minimum thickness is 0.3 mm and the maximum resistivity
is 500 Ohm-m at 90°C. The screen is tightly fitted to the insulation to exclude all air voids and
世界杯预选赛赛程表can be easily hand stripped on site.
Inner Covering; Fillers: For cables with a collective metallic layer or cables with a metallic
layer over each individual cores with additional collective metallic layers, semi-conducting
世界杯预选赛赛程表inner covering and fillers shall be applied over the laid up cores. The inner covering is made
of non hygroscopic material, except if the cable is to be made longitudinally watertight. The
inner covering shall be extruded or lapped.
The approximate thickness of extruded inner coverings is given in Table 2:
|Ficititous Diameter over Laid Up Cores;||Approx. Thickness of Extruded Inner Covering;|
Metallic Layer: The metallic layer shall be applied over each core or applied as a collective
screen. The metallic screen shall consist of either copper tapes or a concentric layer of
世界杯预选赛赛程表copper wires or a combination of tapes and wires. The metallic layer provides an earth
fault current path, capable of withstanding fault current to earth of 1000A for one second at
maximum temperature 160°C. Copper wires are applied over the conducting water blocking
世界杯预选赛赛程表layer with a minimum diameter of 0.5mm. And over the copper wires, copper tape with
世界杯预选赛赛程表minimum thickness of 0.1mm can be applied helically with overlap.
世界杯预选赛赛程表Total cross section of copper wire screen is shown in table 3.
|Nominal Cross-Section Area of Cable||Minimum Cross-Section of Copper Wire Screen Area||DC Resistance of the Copper Wire Screen|
|up to 120||16||1.06|
Separation Sheath (for armoured cable): The separation sheath comprises a layer of extruded PVC, PE or LSZH. The nominal thickness is calculated by 0.02Du + 0.6mm where Du is the fictitious diameter under the sheath in mm. The nominal separation sheath thickness shall not be less than 1.2mm.
世界杯预选赛赛程表Armour (for armoured cable): The armour consists of galvanized steel wire applied over the inner covering with diameter specified as in Table 4.
|Fictitiious Diameter under the Armour||Armour Wire Diameter|
Over Sheath: Overall sheath comprises a layer of extruded either PVC type 9 conforming to BS 7665-4.2 or MDPE type TS2 conforming to BS 7655-10.1; LSZH can be offered as an option. The over sheath is normally black in colour. When a DC voltage test is to be performed on the over sheath, a semi-conducting layer such as graphite coating shall be applied over the surface of the extruded over sheath. The nominal over sheath thickness is calculated by 0.035D+1 where D is the diameter immediately under the over sheath in mm. For cables with the over sheath not applied over the armour, the nominal over sheath thickness shall not be less than 1.4mm. And for cables with over sheath applied over the armour, the nominal over sheath thickness shall not be less than 1.8mm.
Operating Temperature: up to 90°C
Temperature Range: -5°C ( PVC or LSZH sheath ); -20°C ( PE sheath )
Short Circuit Temperature: 250°C (short circuit duration up to 5 seconds)
世界杯预选赛赛程表Bending Radius: 12 x OD
|Nom. Cross- Section |
|Nom. Insulation |
|Copper Tape |
|Nom. Armour |
|Approx. Overall |
Rating of Conductor
世界杯预选赛赛程表There is no news related to this product.
ZMS Cable have a wide product scope, includes: Power cables up to 500kV, AAC, AAAC, ACSR conductors, ABC Cable,electric wires, instrument cable, telecommunications cable, Stay wires. With advanced manufacture technology, rich human resource and effective management system, we guarantee all products are manufactured strictly in accordance with GB, IEC, BS, NFC, ASTM, DIN standards,etc. Beyond quality control, ZMS have been trying its best to offer much higher standard of services rather than expected.